You will need to fix the device to the TCH-B200 hand-held programmer and then press the left grey button. Status messages will display on screen. The address of the device will then be displayed. The default address is 127.
Fix the device to the TCH-B200 hand-held programmer and then press the left grey button. Status messages will display on screen. The address of the device will then be displayed. Pressing the left button increases the address by 10. Pressing the right button increase the address by 1. Press the blue button to store the new address.
Yes, but you will need a PL3 lead (available to order). Plug one end into the TCH-B200 and the other end into the call point or mini-module. You can then program as before.
There are 3 modes available; Polling (flashing LEDs), non-polling (no flashing LEDs), and standard (default). To change the mode of a device you will need to use a TCH-B200 hand-held programmer. Ensure there is not a device fixed to the TCH-B200. Press and hold the right grey button and the blue button together. Press and hold the left grey button until dots appear on screen. Release left grey button after a few seconds. A menu will appear. Release right grey button and blue button. Use the left grey button to change the mode. Use the blue button to store your selection.
Fix the device to the TCH-B200 hand-held programmer. Switch it on using the left grey button. Wait for the address to be displayed. Press the blue button to display the analogue reading. Over time a device may become contaminated; it is therefore important to check that the analogue value still falls within the normal operating range. The normal operating range is printed on the underside of the device.
The default setting for exit signs is maintained. The default setting for luminaires is non-maintained. However, these settings can be changed via the panel.
Again, the default setting for exit signs is maintained, and the default setting for luminaires is non-maintained. This cannot be changed.
No. You will need to order the EL-2 Addressable Control Panel.
No. Even though the products look the same, the protocols are different and therefore they are not compatible.
The RSM-WTM needs to be given a recent reset or drop on reset so the fire panel can reset the wireless translator or FIREbeam; this is configured in the panel software under the output settings of the CHQ-POM. The CHQ-POM when used for a FIREbeam or wireless translator also needs the current limit setting to 22mA .
Removal tool 3 is compatible with the ALN-EN, ATJ-EN and the ACC-EN. Line up the arrow on the removal tool, with the arrow on the underside of the device, push it in and the device casing will release. To put the case back on, line up the arrow on the underside of the case with the line on the side of the device.
No. You must use special dry smoke pellets, not a compressed aerosol.
All of this information is now available on the Hochiki store. Simply click ‘Visit Store' in the top right-hand corner of this page. Once you land on the Hochiki store, you can then search for the product you require using the search bar. There are a number of PDFs available to download on each product page.
Our product support team can be contacted on +44 (0) 1634 266 102 or emailed on firstname.lastname@example.org
If you would like to order directly from Hochiki you will need to open an account. The process will involve a credit check and may take a few days. However, if your requirement is urgent (or a one-off requirement) we have a number of distributors who may have items in stock, or could place an order for you. To discuss opening an account with us or to find where your closest distributor is, please call us on +44 (0)1634 266 570.
The Hochiki store is a brand new online purchasing facility which will shortly be available to all registered customers. To ensure that we are able to support our customers in the most effective way, this will be a phased roll out. Existing customers will be emailed when the online purchasing facility is available to them. If you are not an existing Hochiki customer, you will need to apply to open an account, before we can give you access to the Hochiki store. To discuss opening an account please call us on +44 (0)1634 266 570.
If you have any queries regarding your order please contact customer services on +44 (0) 1634 266 558
Whilst our fault rate stands at an impressive X%, we acknowledge that there will still be times when you need to return items. To learn more about our returns process please go to this link - https://www.hochikieurope.com/documents/Hochiki%20Returns%20Process.pdf As noted on the returns process document, it is imperative to obtain a returns tracking number before you return your item. Please also note that it is our policy not to accept stock cleansed, unwanted or unused products back for credit unless a prior agreement exists with your Regional Sales Manager.